Mobile ground verification for mounting on pressure-vacuum vehicles, bulk trucks and tankers.
Vacuüm trucks and bulk chemical road tankers, including their hoses and hose connections, are susceptible to static charge accumulation during the transfer of product into or out of the truck’s containment system. This accumulation of static charge is equivalent to a hidden source of ignition and if discharged as a static spark can lead to the ignition of the product or the atmosphere in which the truck and material handling team is operating.
The Earth-Rite® MGV is designed to enable operators establish safe earthing of their vehicle in accordance with the recommended practices.
The Earth-Rite® Mobile Ground Verification system (MGV) is a unique, patented technology, designed to provide automatic confirmation of a positive electrostatic earth connection for trucks, collecting and transferring flammable & combustible products.
To eliminate the risk of incendive static spark discharges the API standard 2219: Safe Operation of vacuüm Trucks in Petroleum Service recommends that vacuüm truck operators transferring flammable and combustible product in hazardous locations must fully ground the truck prior to any other task in the transfer operation by connecting the truck to a "proven ground source".
Static Earth Verification
The Earth-Rite® MGV system ensures the connection resistance of the object that is identified as the ground source to earth, is low enough to safely dissipate static charges from the truck.
Continuous Ground Loop Monitoring
When the Static Ground Verification process is confirmed, the MGV system continuously monitors the connection resistance of the truck to this verified grounding point for the duration of the transfer process. This connection resistance must be maintained at 10 ohms (or less) for the duration of the transfer process.
Two Output Contacts
located in the control unit of the Earth-Rite® MGV system can interlock with pumps or other control devices to prevent transfer operations should a static ground connection fail to be established or maintained for the transfer process.
Easy and Quick Operation
Removing the need for taking manual resistance readings or interacting with complex system interfaces the operator activates the system by simply connecting the system’s earthing clamp to a site designated earthing point, buried metal structure (pipes, storage tanks) or temporary points like buried earthing rods.